The reading should be between 0.3 to 2 ohms. If it is 0, there is a short. If it is over 2 ohms or infinite, there is an open. You can also dry the connector and retest to possibly get more accurate results.
What is the resistance of a 3 phase motor?
Most are between 3 and 2.0 ohms. There are 8ohms. A short between phases exists if you read zero.
How many ohms should a motor read?
With a multimeter, measure the resistance between motor frame (body) and earth. A good motor should read less than 0.5 ohms. Any value greater 0.5 ohms indicate trouble with the motor.
How do you know if a 3 phase motor is good?
Using a multimeter, check the continuity of motor winding from phase to phase ( U to V, V to W , W to U ). Each phase to phase must have a continuity if winding is OK. If any particular phase fails the continuity test, your motor is probably burnt.
How do you know if a motor is bad on a multimeter?
To test your motor for short to ground, you’ll need to set the multimeter to ohms and disconnect the motor from its power source. Then inspect each wire and look for infinite readings. Alternatively, if you get a reading of 0, you might have a cable issue.
What is a good megohm reading for a motor?
The rule may be stated: Insulation resistance should be approximately one megohm for each 1,000 volts of operating voltage, with a minimum value of one megohm. For example, a motor rated at 2,400 volts should have a minimum insulation resistance of 2.4 megohms.
How do you find the insulation resistance of a 3 phase motor?
Phase Resistance: Take the insulation tester and set it to 500V. Take each end and place it on different permutations of L1, L2 and L3 and record each reading. Phase to Earth Resistance: Take the insulation tester, using the same setting, and check each lead from phase to the frame of the motor.
Should a 3 phase motor have continuity?
The windings (all three in a three-phase motor) should read low but not zero ohms. The smaller the motor, the higher this reading will be, but it should not be open. It will usually be low enough (under 30 Ω) for the audible continuity indicator to sound.
How do you test a phase sequence with a multimeter?
You can set the Phase Rotation setting on your mutlimeter. Look for terminals labeled L1, L2 and L3 when inspecting the three-phase motor. The jacks that are labeled L1, L2, L3 should be connected to the power wires.
How do you troubleshoot a 3 phase motor?
Examine the motor’s electrical connections and terminals. Remove power to the motor and repair any damaged or loose connections. Remove motor voltage and disengage the motor from the machine that it is running. Reconnect motor voltage and see if the motor now runs.
How do you know if a 3 phase motor is bad?
Check all three wires singly T1,T2,T3 (all three phases) to the ground wire. Readings should be infinite. If its zero or reads any continuity at all, then a problem exists with either the motor or cable . If it is go directly to the motor and disconnect from cable and check motor and the cable separately.